In the activities related to the RenoZEB envelope prototype testing and validation, Focchi team has prototyped and tested further facade panels.
Two tests have already been conducted with positive results:
1) an acoustic mock-up test (on the left) under UNI EN ISO 16283-3:2016/EC 1-2016/EC 2-2016 and UNI EN ISO 717-1:2013 (IN-OUT test) with an acoustic insulation performance moved from 46dB of the only building envelope to 57dB after the installation of the RenoZEB panels;
2) a performance mock-up test (on the right) under UNI EN 13830:2005 passing positively the tests and achieving the standard for CE certification.
In the next weeks, a further test under EN 13823 (classification SBI) will be conducted to understand the reaction to fire of the RenoZEB panel.